Loss lesson - sandwich panel fire
A large fire occurred at the site of a major food processing factory in January 2010, in a semi rural area some 50kms south of Melbourne. The fire started in a staging area for plastic packaging trays, and despite the area being attended and the presence of automatic smoke detection, the fire was able to quickly develop.
The cause of the fire could not be definitively determined. Suggestions were a failed fluorescent light fixture or a drive associated with an overhead conveyor. The fire was detected at an early stage by an operator who unsuccessfully discharged an extinguisher. Despite his best efforts, the fire quickly spread to the EPS (expanded polystyrene) sandwich panel ceiling.
An evacuation was initiated and the fire brigade called. By the time the volunteer fire brigade arrived with their first unit, some 10-15 minutes into the fire, flames were erupting through the steel deck roof over half the length of the building. Before the fire fighters could mount any first attack, the fire had spread the full length of the main production building, associated loading dock and cold store, overall a length of around 100 metres.
Over 100 fire fighters eventually attended and were able to contain the fire to the main building and protect the large ammonia receivers adjacent to the building. A total loss of the production building resulted in major business interruption requiring some nine months of expensive temporary outsourcing and some loss of business.
The key lessons coming out of this fire was a reinforcement of previous experience:
- EPS panel ceilings are very susceptible to fires starting beneath them
- Fires under EPS panel ceilings spread very rapidly, the fire spreads across the ceiling as the panels progressively delaminate and the EPS melts and vapourises to fuel
- Fires can also spread inside wall and ceiling panels, before bursting out at the panel seams
- The fire load from EPS wall and ceiling panels is enough on its own to cause deformation and collapse of major steel roof beams
- Fire brigades are unlikely to contain a developed EPS panel fire and they will not enter the building due to the risk of collapse.
An interesting footnote to this fire was the performance of approved PIR sandwich panels. A new extension to the existing EPS cold store had been constructed from PIR. The fire burnt up to the PIR wall but did not penetrate, the PIR section was left largely intact. This tends to confirm our recommendation of approved alternative panels, be they PIR or Phenolic resin matrix.
Zurich Australia's Property insurance options
|Type of cover||What this cover provides||How to purchase|
|Enables you to conveniently tailor-make one insurance policy to protect your business. With Zurich you can select from our range of business insurance options to suit your business needs.||Through an insurance broker Find out more|
Zurich has now ceased offering strata policies and we will cease renewing strata policies with policy renewal dates effective as of 15 March 2016.
All existing strata policies will remain valid and in force until their scheduled expiry date.
All claims will be managed in the normal process.
For further information please contact your broker.
|Provides cover for losses arising from interruption or interference to the business following Plant or Equipment failure and works in conjunction with the Zurich Engineering Plant Insurance or Zurich Electronic Insurance Policies, to protect profits that would be affected by Insured Damage.||Through an insurance brokerFind out more|
|Suitable for enterprises with assets generally greater than $10 million. We prefer writing business within the manufacturing area where your risk engineering, financial and claims experience is above average.||Through an insurance brokerFind out more|